Part of the BACHARACH family of products. HGM / RDM Refrigerant Gas. Monitoring System. Refrigerant Gas Detection,. Identification & Monitoring. Refrigerant monitoring system • Read online or download PDF • Bacharach HGM User Manual. View and Download Bacharach HGM installation, operation & maintenance instructions manual online. Refrigerant Gas Monitoring System. HGM
|Published (Last):||24 October 2013|
|PDF File Size:||20.48 Mb|
|ePub File Size:||1.76 Mb|
|Price:||Free* [*Free Regsitration Required]|
Use any of the remaining service knockouts to gain access to the interior of the monitor. Page 8 The HGM should be centrally located baxharach the mechanical room and be readily accessible for easy visual monitoring and servicing. To print the manual completely, please, download it. It offers a wide variety of displays bacnarach can fully program any associated monitor.
The default value is feet. If you are unfamiliar with this information, please reference the HGM operations manual. The enclosure utilizes keyhole mounting brackets designed for 12 pan head fasteners.
This can take some several minutes since it is dependent upon how many zones there are and their lengths.
Combustion analyzer standard efficiency equations, siegert efficiency equations, and nsx version 87 pages.
Fault Log Register Register 0x, 0xh bytes These registers contain the 20 most recent fault events, the time they occurred, and a pointer to the most recent event. Use any of the remaining service knockouts to gain access to the interior of the RDM The second is a PPM reading normalized to standard temperature and pressure. Parameters must also be hgm30 for each HGM monitor connected to the network.
Page 67 Programming New Gasses As new refrigerants come into use the HGM allows hgm30 addition of these new gases to its on-board refrigerant gas library. The default is 60 minutes. The monitor should be installed out of direct sunlight in a clean, dry area that is not subject to temperature or humidity extremes. Connect the sample bag directly to the intake port for the zone you have set up and allow the HGM to sample the entire bag.
After a brief moment the System Screen is displayed. Service Pursuant to the stated warranty, Bacharach, Inc. Programming New Bachzrach As new refrigerants come into use the HGM allows bqcharach addition of these new gases to its on-board refrigerant gas library. By pressing ‘print’ button you will print only current page. Don’t have an account?
Enter text from picture: Page 84 It is strongly recommended that any New Gas curves that are added be done in conjunction with help from Bacharach, Inc. The first bachzrach contains bytes and the second register contains bytes. This is the correct setting if the RDM is connected to only one HGM, or if it is the last device on a network chain.
Page 87 Fault Log Register Register 0x, 0xh bytes These registers contain the 20 most recent fault events, the time they occurred, and a pointer to the most recent event. Appendix Appendix Instruction Page 69 LINE 7: The data is split into 2 registers.
Bacharach HGM300 Installation, Operation & Maintenance Instructions Manual
Press the adjacent key to adjust the setting. General Operation The RDM operates by polling the network approximately once every 12 seconds to determine the current status of the HGM monitors. This parameter can be changed from Zone Setup Screen 1 Page The interface ygm300 plugs into the socket provided on the main circuit board, and the external devices are then cabled to the HGM as described earlier in this manual.
RDM Mounting Specs Installation Hold the display module flat against the mounting surface and allow it to slide down engaging the screw There are two versions of PC software. Bacharach hgm to johnson metasys n2 communications adapter electrically isolated n2 port version 10 pages.
All pending alarms across the entire network must be acknowledged before the RDM returns to normal operation. Don’t bachsrach me this message again. Press the adjacent key to adjust the value. For example, at the default scale factor of 0. The fresh air purge line should draw from an area that does not contain any refrigerant gas and cannot exceed feet in length. The HGM should be centrally located in the mechanical room and be readily accessible for easy visual monitoring vacharach servicing.
Bacharach HGM Halogen Gas Monitor | LEL International
Page 60 Repeat this procedure to acknowledge any remaining alarms. It is strongly recommended that any New Gas curves that are added be done in conjunction with help from Bacharach, Inc.
These values must match the dip switch settings on each HGM circuit board.